4.1 The maximum operating temperature of the conductor of the cable is 90℃
4.2 When short circuit(the longest duration does not exceed 5S)the maximum operating
temperature of the cable conductor is 250,and the overoad temperature is no more than 130.
4.3 When laying the ambient temperature is not less than 0 degrees Celsius,
the temperature of the enviroment of the cable laying is not less than -15℃
4.4 Bending radius(Table 1)
4.5 When laying is not limited by the level of gap.
4.6 The fire resistance of the cable meets the requirements of the GB/T19666-2005 standard.
5. Product model(Table 2)
6. Cable structure size(Table 3 to table )
6.1 0.6/1KV XLPE power cable structure size
Room 2106, Rongsheng Plaza, Chang’an District, Shijiazhuang, Hebei, China
Tel.: +86-138 3311 9023
For more details, please visit pdf :XLPE Insulated Power Cable With Rated Voltage Of 0.6/1KV